Your Price: $2341.95
Pressure drinking water cooler shall deliver at least 8 GPH water at 50ºF (10ºC) cooled from 80ºF (26.7ºC) inlet water at 90ºF (32.2ºC) ambient. Front mounted push pad requiring less than 5 pounds of force to activate shall initiate water flow through a flexible hooded bubbler having a non-squirt feature. Bubbler shall operate between 20 and 120 psig and have an adjustable stream regulator to control water flow. Stainless steel fountain basin shall have removable drain strainer. Cooler assembly shall have cup dispenser, cup filler and waste bin attachment. Exterior panels shall be stainless steel. Chiller system shall use R-134a refrigerant, system shall be hermetically sealed and refrigerant flow shall be capillary tube controlled. An adjustable thermostat having an off position shall control refrigeration system. Mounting frame shall be provided for installation. Potable water system components shall comply with the Safe Drinking Water Act Amendments, the 1988 Lead Contamination Control Act and shall be Certified to NSF/ANSI 61, Section 9. Chilled water capacity shall be rated per ARI Standard 1010. Drinking water cooler shall comply with ANSI A117.1-1992 and ADA parallel approach requirements when properly installed. Chiller shall be Listed by Underwriters Laboratories Inc. to U.S. and Canadian safety standards. Drinking water cooler shall be Sunroc model NFRD8CD.