The Oasis R1P remote water chiller shall deliver at least 1.0 gph of water at 50°F cooled from 80°F inlet water at 90°F ambient. Evaporator shall be copper evaporator tube on stainless steel water storage tank and both shall be encapsulated in insulation. Total water system shall be stainless steel. R-134a refrigerant system shall be hermetically sealed and refrigerant flow shall be capillary tube controlled. Drinking water chiller R1P has an adjustable thermostat having an off position shall control refrigeration system. Potable water system components shall comply with Safe Drinking Water Act Amendments, the 1988 Lead Contamination Control Act and shall be Certified to ANSI 61 Section 9. Chilled water capacity shall be rated per ARI Standard 1010. Cooler shall be Listed by Underwriters Laboratories Inc. to U.S. and Canadian safety standards.
Oasis R1P Category:
Have you purchased this product?
If so, get paid for your feedback! We value your input at PittsburghWaterCooler.com. Log in and leave a review to tell us and our future customers what you thought about it.