The Halsey Taylor SJ1 / SJ1-Q Water Chiller delivers 1.3 GPH of 50°F water at 90°F ambient and 80°F inlet water. Designed for use with any drinking fountain. Compressor is hermetically sealed. Manufacturer certifies unit to be lead free as defined by the Safe Drinking Water Act. System controlled by adjustable thermostat. Complies with ARI Standard 1010.
No Lead Design:
These water chillers are certified to be lead-free as defined by the Safe Drinking Water Act. Halsey Taylor water chillers are manufactured with a waterway system utilizing copper components and completely lead-free materials. These waterways have no lead because all lead materials, such as leaded brass, have been removed. All joints are brazed using silver solder only. No lead solder is permitted. A strainer with an easily cleanable screen is provided to allow trapping and convenient removal of waterborne particulate of 140 microns and larger prior to their entry into the water cooler.
- Fountain Cabinet:
Manufactured of rust-resistant heavy gauge galvanized steel. Front and rear panels removable for servicing.
- Plumbing Connections:
1/4" O.D. stainless steel tubing inlet and outlet.
- Electrial Connection:
7/8" diameter opening for conduit connection.
- Cooling Unit
Tank style evaporator. Tank is stainless steel, with drain plug. Fully insulated.
- Temperature Control:
Positive sensing thermostat for controlling temperature of evaporator/chiller storage water. Factory set for 40°F water. Adjustable to 50°.
- Refrigeration System:
Hermetically sealed, positive start compressor with lifetime lubrication and built-in overload protection, efficient capillary sizing, large capacity dryer-strainer, and self-lubricated fan cools copper/aluminum condenser. System uses R134A refrigerant. Test pressures, highside 325 psig., lowside 140 psig. Protected by Halsey Taylor's Limited 5 Year Warranty.
This unit is suitable for installation underneath a conventional kitchen sink, in a cabinet not less than 36" (914mm) wide (inside dimension). Two air openings with a minimum of 40" square (1016mm/square) each, minimum of 75% open area, must be provided in the cabinet. One opening must be in the overhang of the toe space and the other opening near the top of the cabinet. The remote unit must be installed with a minimum of 3" clearance between the unit and the rear wall of the cabinet. It can be installed flush against either side wall of the cabinet. The side louvers which are not against the cabinet must not be blocked by objects located within 4" (102mm) of the louvers. In addition, a minimum of 1" to 2" (25 to 51mm) clearance must be provided between the toe space air opening and the front of the unit.
Furnished with 6" leads enclosed in junction box for direct connection to standard 115 volt, 60 Hz, single phase.
|Manufacturer ||Halsey Taylor|
|Model # ||SJ1|
|Cooling Capacity ||1 GPH|
|Freeze Resistant ||No|
|Outdoor Rated ||No|